KNX ENO 636 secure
Bi-directional , graph. display , surface-mounted housing
Gwarancja producenta: 2 lata
KNX ENO 636 secure
The KNX ENO 636 secure device serves as a bidirectional gateway between EnOcean wireless devices and the KNX bus. With this device, commands and measured values from EnOcean wireless sensors can be transmitted to the KNX bus, for example to control KNX actuators.
As the first KNX gateway in the market, the new KNX ENO 636 secure supports the encrypted radio communication with EnOcean devices. Commissioning is as simple as usual: with all 32 channels encryption can be activated individually. Subsequently EnOcean sensors and actuators, which support security, can be taught as before. The user gets more security without loss of comfort.
Broad variety of functions and 32 channels
The KNX ENO 636 secure has 32 channels, which can be used with one of the following functions from over 100 profiles (EEP EnOcean equipment profiles):
Link from EnOcean sensor to KNX:
- Switching and contact functions
- Shutter up/down
- Window contacts
- Window handles
- access cards switches
- push button switches
- Temperature sensors
- Humidity sensors
- Light sensors
- Presence sensors
- Gas sensors
- Room control devices
- Automated counter devices
- Environmental sensors (weather station)
- Digital inputs
Link from KNX to EnOcean actuator:
- HVAC actuators (valves)
Control / logic:
- Tracking circuit
- Two point controller (byte and float)
- Continuous regulator
- Heat demand requirements
- Lighting control
- Logical functions
- Gates (e.g. AND, OR, XOR)
The configuration of the device and the channels is done using the ETS software via the KNX bus. For the teach-in of the wireless components the keys and the display in the device are used.
Mounting and connection
The mounting can be done on a wall surface (e.g. brick-work or wood). The mounting holes match for a 55 mm flush-mounted box. The power supply of the device is realized via the bus.
The repeater function is used for extend distances between sensors and actuators. The KNX ENO 636 is a so-called level-1 radio repeater.
Bus monitor function
The integrated bus monitor function is used for system diagnostics directly on the device. The device can display both EnOcean telegram as well as KNX telegrams.
Configuration: KNX ENO Tool
The KNX ENO Tool software can be used to configure the Links between various EnOcean-Sensors and the KNX/EIB EnOcean-Gateway KNX ENO 626/630/632/6347636. The device configuration of the Gateway can be read, modified, exported and saved back to either the same or another Gateway. EnOcean Bus Monitor showing the EnOcean Telegrams send over the KNX Bus.
- Housing: plastic, white
- Surface mounting, matches on 55 mm flush-mounted box
- Dimensions: 81 x 81 x 25 mm
- KNX Bus approx. 12 mA
- Connector for KNX Bus (red / black)
- EnOcean, ISM Band 868,3 MHz, ASK
- Output power: 3dBm
Mogą Ci się spodobać też: